Application: Service penetrations – plastic SWD systems Fire Resistance Period: EI 120 up to EI 180 Insulation/integrity: Insulation and integrity Test Standard: BS EN 1366-3: 2004 Approval Type: CE Mark – 1121 CPD – JA5003
Pyroplex® CE Marked Pipe Wraps have been specifically designed to reinstate the fire resistance of a wall or floor which has been penetrated by services such as plastic flammable pipes used in soil, waste and drainage services.
Pyroplex® CE Marked Pipe Wraps are available in two fire ratings; 2 hour and 4 hour. To fit, simply fix wrap around the pipe using adhesive tab and slide along pipe into wall/floor cavity. After insertion the cavity around the pipe can be made good with filler.
Pyroplex® Limited have carried out numerous independent fire resistance tests to confirm the suitability of the product and to demonstrate product compliance by utilising BS 476: Part 20: 1987 and BS EN 1366-3: 2004. EN classification report to BS EN 13501-2: 2007 is available for download on Pyroplex® website. Pyroplex® 200 series wraps refer to EN Classification reports WF174256/C Issue 2. Pyroplex® 400 series wraps refer to EN Classification reports WF174256/D Issue 1.