Application: Service penetrations – plastic SWD systems Fire Resistance Period: up to EI 240 Insulation/integrity: Insulation and integrity Test Standard: BS EN 1366-3 Approval Type: CF 635/CE Mark – 1121 CPD – JA5003
Pyroplex® CE Marked Pipe Wraps have been specifically designed to reinstate the fire resistance of a wall or floor which has been penetrated by services such as plastic flammable pipes used in soil, waste and drainage services.
Pyroplex® CE Marked Pipe Wraps are available in two fire ratings; 2 hour and 4 hour. To fit, simply fix wrap around the pipe using adhesive tab and slide along pipe into wall/floor cavity. After insertion the cavity around the pipe can be made good with filler.
Pyroplex 200 series wraps are now available in an extended range of sizes, suitable for a wide range of pipe diameters, pipe materials and can be used for a range of pipe thicknesses. For additional information please see the technical datasheet.
Pyroplex® CE Marked Pipe Wraps have achieved a fire rating of either 2 hour or 4 hour.
Easy to place around pipe and slide into position.
Intumescent material is totally unaffected by water, is robust, ‘non-flaking’ and difficult to tear.
Colour coded: Red sleeve 200 series, and Silver sleeve 4 hours.
Pyroplex® Limited have carried out numerous independent fire resistance tests to confirm the suitability of the product and to demonstrate product compliance by utilising BS EN 1366-3. EN classification reports to BS EN 13501-2 is available for download on the Pyroplex® website.
Pyroplex® 200 series wraps refer to EN Classification reports WF174256/C Issue 2 and 387452 Issue 1. Pyroplex® 400 series wraps refer to EN Classification reports WF174256/D Issue 1.