Application: Service penetrations – plastic SWD systems Fire Resistance Period: up to 240 minutes (dependant on application) Insulation/integrity: Insulation and integrity Test Standard: BS 476: Part 20: 1987 and BS EN 1366-3: 2009 Approval Type: Certifire CF635 / CE Mark 1121-CPR-JA5002
Pyroplex® CE Marked 400 Series Pipe Collars have been specifically designed to re-instate the fire resistance of a wall or floor which has been penetrated by plastic flammable pipes used in soil, waste and drainage services.
They will seal closed flammable pipes from 25mm to 400mm diameter and can be face fixed in a wall or ceiling structure.
They are suitable for use on concrete, masonry and plasterboard partitions.
Ensure substrate around pipe is flat and free from obstructions – if necessary make good by using Pyroplex® Intumescent Acrylic Sealant.
Release retaining pin and position pipe collar around pipe.
Slide the tab through slot in pipe collar and fold back 180 ° to secure.
Secure pipe collar by drilling holes in structure by using fixing lugs as template. To fix use M8 x 65mm sleeve anchors or 50mm [minimum] expanding bolts. Do not use plastic raw plugs and or plastic sleeve anchors.
When the collar has been securely fitted into place any residual gaps between the collar and the substrate can be filled using Pyroplex® Intumescent Acrylic Sealant.
Pyroplex® CE Marked 400 Series Pipe Collar is tested to BS 476: Part 20: 1987 and BS EN 1366-3: 2009 and has a European classification in accordance with BS EN 13501-2: 2007 +A1: 2009. Pyroplex® 4 hour Pipe Collars are compliant with the requirements given in CERTIFIRE TS03. CERTIFIRE Certificate No. CF635 EC Certificate of conformity 1121 – CPD – JA5002.