Application: Service penetrations – plastic SWD systems Fire Resistance Period: 120 minutes Insulation/integrity: Insulation and integrity Test Standard: BS 476: Part 20 and BS EN 1366-3 Approval Type: Certifire CF635 / CE Mark 1121-CPR-JA5002/ETA 15/0136
Pyroplex® CE Marked 200 Series Pipe Collars have been specifically designed to re-instate the fire resistance of a wall or floor which has been penetrated by plastic flammable pipes used in soil, waste and drainage services.
They will seal closed flammable pipes from 55mm to 160mm diameter and can be face fixed to a wall or ceiling structure. They are suitable for use on concrete and masonry partitions.
Pyroplex® CE Marked 200 Series Pipe Collar is tested to BS 476: Part 20 and BS EN 1366-3 and has a European classification in accordance with BS EN 13501-2. Pyroplex® Pipe Collars are compliant with the requirements given in CERTIFIRE TS03.
1. Ensure substrate around pipe is flat and free from obstructions – if necessary make good by using Pyroplex® Intumescent Acrylic Sealant around the perimeter. 2. Release retaining pin and position pipe collar around pipe. 3. Slide the tab through slot in pipe collar and fold back 180˚ to secure. 4. Secure pipe collar by drilling holes in structure by using fixing lugs as template. To fix use M8 x 65mm sleeve anchors or 50mm [minimum] expanding bolts. Do not use plastic raw plugs and or plastic sleeve anchors. 5. When the collar has been securely fitted into place any residual gaps between the collar and the substrate can be filled using Pyroplex® Intumescent Acrylic Sealant.
Pyroplex® Limited have carried out numerous independent fire resistance tests to confirm the suitability of the product and to demonstrate product compliance by utilising BS 476: Part 20 and BS EN 1366-3. EN Classification report to BS EN 13501-2 is available to download.